Troubles with the cooling system are indicated when you find the coils have frozen. At this time, due to the importance of the situation, we at Hal Mechanical would like to discuss how the ice develops on the air conditioner.
Low Refrigerant Levels
When there are low levels of refrigerant, ice can be created on the unit. The level of refrigerant inside your coils is essential. When the refrigerant is compressed, it releases the collected heat. The dropped pressure occurs when the gas refrigerant is changed from the liquid. The conversion happens too early when there is not enough refrigerant in the system from the lack of pressure. The condensed moisture on the coils will then freeze.
Blower Motor Not Working
A major element of the cooling system is the blower motor. No matter if it is the spinning motor itself or the blower motor’s run capacitor, it causes the air to stop flowing quickly enough over the coils no matter should the blower fan stops blowing. The frozen coils are the result when the air stops blowing. You will likely hear irregular or rattling sounds from your air conditioner in the event the blower motor is in the process of failing.
Dust Buildup on Coils
With debris and moist air condensing on the cold surface, it leaves layers of dust on the refrigerant coils that becomes compacted resulting in frozen coils.
Weak Air Flow
The air conditioner unit is known to freeze over when there is not enough air flow. From the blower motor to the air intake, it can be challenging to identify the cause as there are many problems contributing to the poor air flow. It stops warm air from flowing over the coils while the compressor continues run when the airflow in the system is impeded.
In order to distribute the air throughout the home, the air ducts are essential. The airflow cannot reach the coils should the ducts be insufficient in dispersing the air. The cooling systems airflow is lost from flawed air ducts, even if the system is running smoothly. The coils begin to freeze because there’s not enough warm air to manage the temperatures.
Low Voltage Fan
Since the air conditioner requires electricity to a variety of high-power components to run if the air conditioner becomes a central part of your summer power. While the compressor keeps running, problems can occur as well when your fan or blower motor are receiving enough power.
Clogged Air Filters
Neglecting the air filters is all too common for homeowners. The coils will freeze since the airflow is extremely restricted when the filters are clogged and blocked.
Emergency Central Air Conditioning Repair in Aliante, Anthem, Desert Shores, Eldorado, Enterprise, Green Valley Ranch, Henderson, Inspirada, Mountain’s Edge, North LV, Peccole Ranch, Paradise, Providence, Rhodes Ranch, Seven Hills, Silverado Ranch, Spring Valley, Summerlin, Sunrise Manor, The Lakes, Tuscany Village & Las Vegas Nevada
You need to promptly use the thermostat to shut off the system if you discover the coils are frozen. This will help to prevent further damage as well as let the ice thaw. In the event you discover the air conditioner has a buildup of ice, be sure to call Hal Mechanical.